Angle Thermostatic Radiator Valve – PVC
|13.40.001||1/2″ Angle Thermostatic Radiator Valve – PVC||30|
|13.40.014||1/2″ Pex-B Angle Thermostatic Radiator Valve – PVC||30|
ANGLE THERMOSTATIC RADIATOR VALVE – PVC
PEX-B ANGLE THERMOSTATIC RADIATOR VALVE – PVC
INSTALLATION and OPERATING INSTRUCTION
1- Make sure there is no damage on the product may occur during transport and shipping. Before assembly do not unpack
the product in order to prevent from the external effects.
2- Clean all kinds of contaminants before assembly.
3- Make sure that the thread length to be connected to the valve is not too short or too long than the thread length of the
4- Keep the valve in closed position during installation. Install the valve with the appropriate tool from the side where you’ll
5- Use enough flax or plumping adhesive.
6- Do not paint the valve, do not expose the valve with abrasive chemicals,
7- Do not open or close with any other tool.
8- Pay attention to on header signs by taking into account heat requirement while use valve.
9- The boiler temperature must be higher than the temperature of the thermostat that is set; otherwise, if the circulation
pump is switched on, the flow sound hear from valve.
10- Set cursor to Max. grade at regular intervals and tighten connection nut to fix the gap.
11- The cap should be set to Max. grade during the summer months.
12- The cap should be set to (*) this position during the winter months.
13- (O) does not indicate close position. Not bring to this position during the winter months .
14- Use filter in the installation to keep cleanly to apartment entrance
15- Do not hang anything on the cap.
16- The pressure balancing valves should be used in floor entrance to supply quiet working and prevent uneven flow of
thermostatic radiator valve.
17- To supply quiet working, the maximum pressure changing must not exceed 30-35 kPa.